You might have other loads on your line and this is a possible reason for the breaker tripping. A dedicated line would definately be in order. Did you install a dedicated line? Did anyone mention it might be better to put in a 30a. line? What does B&K recommend? If they say a 20a would be enough and the problem persists then it must be something w/the amp or your wiring. I personally would install a 30a dedicated line, but I do not know the specifics on your amp. Just my opinion, Bill.
2 responses Add your response